2-10. PREPARATION FOR MOVEMENT - continued
For steps I through r refer to figure 2-22.
ù Fuels are toxic and flammable. Avoid breathing of fuel vapors. Keep open flame and sparks away
from filter-separator, fuel hose, and spilled fuel.
ù Do not touch metal parts with bare hands when operating under arctic cold conditions. Frostbite can cause
ù Always wear arctic mittens when handling equipment. Refer to system pump technical manual.
ù Exercise care to prevent injury when removing the ground rod. Wear gloves. Do not hold grounding rod above
To avoid burns, wear hand protection when removing air duct. The air duct and shroud may be
Pull locking arms (1) up and out from filter-separator inlet coupling (2) and disconnect inlet hose assembly (3)
from inlet coupling.
Install dust plug (4) in inlet coupling (2) and push back against locking arms (1) to secure d
ust plug in inlet
n. Install dust cap (5) on inlet hose coupling (6) and push back against locking arms (7) to secure dust capon inlet
o. Loosen clamp (8) and disconnect system air duct (9) from the hot exhaust inlet (10).
p. Disconnect connectors (11) on ground cable (12) from grounding stud (13) and grounding rod (14). Stow
grounding cable (12) under tank on filter-separator.
q. Remove ground rod (14) from ground by sliding hammer (15) up and down on rod.
r. Stow ground rod(14) in bracket (16 and 17).
s. Place hold-down plate (18) on top of bracket (17) and secure in place by tightening the threaded bar (19).