OPERATING PROCEDURES - continued.
Provide an adequate container and open the manual drain valve to drain any accumulated water. Refer to
the draining water from pump procedures in para 2-6.
Stop the system pump. Refer to pump technical manual.
Close the up-stream and down-stream valves to isolate the filter-separator from the system.
Open air vent valve. If,shutdown is temporary, leave open until system is restarted. Refer to the air
purging procedures in para 2-6.
LOCATION OF DATA AND IDENTIFICATION PLATES,
Location of identification plates, instruction plates, and markings for the 200 GPM filter-separator are shown in figure 2-