ASSEMBLY AND PREPARATION FOR USE - continued.
Do not touch cold metal parts with bare hands when operating under arctic conditions. Frostbite
can cause permanent injury.
h. Tank Filling Procedure
. (Refer to Figure 2-14).
Set the 200 GPM filter-separator controls as follows:
(a) Air Vent valve (1) - CLOSED.
(b) Water Drain valve (2) - CLOSED.
(c) Defrost door (3) - second notch of adjustment range.
Open an upstream blocking valve slightly to fill the filter-separator slowly with as little pressure as possible.
Refer to system technical manual.
Start the system pump assembly. Refer to pump assembly technical manual. 2ND NOTCH
Figure 2-14. Tank Filling Procedures- Setting Controls