2-11. Stopping Procedure. (Figure 2-4)
a. Stop the system pumping unit. Refer to applicable system pumping technical manual.
b. Close the inlet blocking, valve
c. Close the outlet blocking valve.
d. Open the manual vent valve (1) by pushing valve down slightly. Close after venting.
If the filter/separator is not to be in frequent use, drain the tank Use following instructions.
Do not drain fuel from the unit on the ground. Drain fuel into a container that can be
closed, otherwise fire hazard or environmental contamination could result.
Use protective equipment to prevent skin and eye contact with fuel.
e. Open manual vent valve (1) fully.
f. Open water drain cock (2) and drain tank (3).
g. Close water drain cock (2) and manual vent valve (1).
h. Remove adapter (4).
i Clean inlet plug (5) and outlet cap (6) and install.